Inverter driven air conditioning is more energy efficient, cheaper to operate and more profitable to install than its non-inverter driven equivalent. Here Neil Ballinger, head of EMEA at automation parts supplier EU Automation, explains how HVAC engineers can maintain the inverters in their customer’s aircon units.
Do you remember cross country at school? It was exhausting; miles of seemingly pointless jogging and sprinting and, if the teacher was not looking, walking. If you were unlucky enough to be born before modern safeguarding measures were introduced, it probably also meant getting lost in the nearest woods.Why isn’t every installation an inverter driven unit, instead of the traditional single stage or dual stage models?
My PE teacher, who seemed particularly vicious at the time, but in retrospect just knew about sports science than most, used to make us do something called fartlek as well. This meant long distance runs, incorporating elements of speed training by mixing up sprints with jogs and walks.
The worst bit was starting to run again after a walk. That is exactly how the motor in your customer’s air conditioner feel if the units you fit are not inverter controlled. The motor has to act just like a runner doing fartlek — it sprints continuously, operating at full speed until the thermostat tells it the room is cool, then it stops. When the room gets warm, it starts again, powers immediately up to full speed and repeats the process indefinitely.
Just like a teenage cross-country runner, it is the starting and stopping that is the tough bit. Furthermore, the unit probably doesn’t have to run at full speed to keep the room at the correct temperature, if the motor were inverter controlled it would speed up and slow down as the temperature fluctuates.
Why isn’t all aircon inverter driven?
We all know that inverter driven aircon is better than its non-inverter driven cousins. It can provide heating as well as cooling and the lifetime cost of use is less for the customer — because their energy bills stay low. The cost of installation is also higher because it is a more complex job, so it works out better for the contractor. It’s a win-win.
The research firm Technavio even lists it as one of the key technologies driving growth in the HVAC market in its annual reports every year. So, the only question is, why isn’t every installation an inverter driven unit, instead of the traditional single stage or dual stage models?When contractors contact EU Automation to buy automation parts, for the units they maintain, they have given us another reason: maintenance
Cost is a factor, but when contractors contact EU Automation to buy replacement motors and inverters, and other automation parts, for the units they maintain, they have given us another reason: maintenance.
As HVAC engineers, we are not necessarily specialists in power electronics, and this makes inverter maintenance daunting. Microcontrollers and IGBTs (Insulated Gate Bipolar Transistors) are not beyond us by any means, but they can be intimidating. Personally, I would back an electrical or heating engineer over an electronics specialist in a problem-solving contest all day long; but that doesn’t solve the problem at hand.
Furthermore, while we are experts in air conditioning brands, and know our Daikins and Grees from our Mitsubishis and Fujitsus, we don’t necessarily have contacts at the inverter manufacturers. Amtech, Danfoss, Vacon and Yaskawa are all names we know, but the local dealer for any of them is probably not in your phone book. This is especially true if the unit you need is from a first-generation inverter driven aircon unit and well over a decade old.
|While we are experts in air conditioning brands, and know our Daikins and Grees from our Mitsubishis and Fujitsus, we don’t necessarily have contacts at the inverter manufacturers|
While inverter maintenance can be daunting, it isn’t difficult. The tools you will need most often are nothing more than a rag and a spanner, while the more esoteric kit is stuff you probably carry anyway, a laptop, vacuum and a Fluke meter.
Before you start, remember that while we tend to refer to an inverter as an inverter, the manufacturers themselves, and many of the sources of information online, often refer to them as VSDs (Variable Speed Drives), VFDs (Variable Frequency Drives) or just plain old drives.
As a result, when you are searching online for a video to explain something, it’s worth using all three of those terms, alongside the inverter manufacturer’s name and the problem to make sure you get the right result.While inverter maintenance can be daunting, it isn’t difficult
When you do move on to maintenance, step one is simple; make sure that the unit is free of dust. This is as easy as vacuuming the heatsink with an ESD (Electrostatic Discharge) vacuum cleaner when you perform routine maintenance or investigate a problem.
While you are checking for build up of dust and daily grime, check the filters. They will probably have to be replaced during annual maintenance, but high use might mean they need to be replaced more often.
The control panel itself should be well ventilated and free of dust as well, if it isn’t it can overheat, which is the number one cause of inverter damage and the most common reason contractors contact us for replacement units.
Before you put your vacuum and duster away, you should make sure that the inverter unit’s location is clean and as sheltered from the elements as possible. Because it’s normally situated on a roof, it’s not going to be perfect, but the units are designed to take a limited battering. That doesn’t mean it’s okay for them to be covered in leaves, surrounded by rubbish or immediately beneath the guttering outlet though!
|Before you put your vacuum and duster away, you should make sure that the inverter unit’s location is clean and as sheltered from the elements as possible|
Get out the spanner
Once you’ve finished these steps, you are done with dusting for now, it’s time to get out your screwdriver and your spanner.
Step one is to make sure the fans on the inverter are operating normally, without noise and with nothing blocking their rotation. The fan keeps the internal components running effectively, just as it does on PC, and if its function is impaired the capacitors will overheat and the inverter will fail.When you install or maintain an inverter on an air conditioning system, it is a sensible precaution to back up the drive parameters to your laptop
The next job is to grab your spanner and make sure the power terminals are on tight. Loose connections cause arcing, overheating and even melting of components and are easily checked during any kind of maintenance and repair.
While we are still in the realms of the work your apprentice can do with their eyes closed, you should also make sure that the inverter’s removable LCD control pad is stored sensibly and not continually attached to the drive. If it remains attached, there is a chance the display will stay on permanently, which means that when you need it to diagnose a problem, it will probably already be burnt out.
Break out the laptop
When you install or maintain an inverter on an air conditioning system, it is a sensible precaution to back up the drive parameters to your laptop. It takes minutes and is normally done by using the removable LCD control. In fact, it’s often as simple as selecting ‘PARs’ and then ‘BACKUP’ from the menu. If you struggle, there are lots of videos on YouTube, like this one, which explain the process for each drive.
As a result, if the inverter ever does need replacing, you can whip out your backed up parameters and order a new or refurbished one easily, before reloading the parameters to the replacement and getting up and running in no time. Your customers will think you are a power electronics genius, as well as a HVAC expert, and they will be loyal for life; especially of you save them on a hot day!
If you follow these simple measures, you will find that the inverters in your customer’s air conditioning units last much longer and no motors will have to run the equivalent of a cross country, thanks to a lack of inverter control.